Control valve plays a major role in every industry from controlling fluid flow to controlling temperature, level, pressure and direction too.
Due long service wear and tear can happen and also it's drift too from a position which can lead to wrong reading and also cause a fatal accident.
To avoid such issue and incident we have to regularly check the control valve by stroke checking.
In this article, we will be discussing stroke checking of the control valve.
Do the connection as shown in the below figure.
To do the connection using loop calibrator we have select source option to feed mA.
We can apply 4mA, 8mA, 12mA, 16mA, 20mA and check scale corresponding mA. If any error exists then we have to calibrate it.
To do calibration adjust zero screw for 4mA adjustment and adjust span screw for 20 mA adjustment.
Check 12mA, 12mA, 16mA and make an adjustment if necessary.
To do stroke check using HART follow blow step (Emerson 475);
1. Go to "service tools" then "diagnostics" and here you can find an option of "stroke check". Here you will receive a warning to make a loop out of the service we have to select this option.
2. Now here you can find four option,
- Ramp to open
- Ramp to closed
- Ramp to target
- step to target
Now we have question that what is the difference between ramp and step.
Here step to target means if our valve position is at 0% and we want to open it 50% in once then we have to select the step to target option.
By selecting Ramp to open, closed or target if we want a valve to open 50% it will heading towards it slowly.